**OsecoElfab’s MV-RF Explosion Vents**

OsecoElfab’s MV-RF explosion vent is an all metal design using a stainless steel controlling membrane (no fluoropolymer). No holes or slits are visible, which makes the MV-RF vent excellent for applications, such as bag houses or bulk storage units, where product build-up may be a concern. The vent may be exposed to system pressures up to 60% of the stamped burst pressure. The MV-RF is also available with FDA-approved gaskets for use in sanitary service applications.

The MV family offers an industry-leading performance tolerance of +/- 0.25 psig. Each vent features design characteristics that reduce the maintenance required while offering a longer service life. All vents meet the requirements of the OHSA Combustible Dust National Emphasis Program and NFPA 68. A 10-day lead time is available for common sizes of MV-RF, MV-CD and MV-RF through our MV vent stocking program.

- The MV-RF is available in sizes ranging from 8”x8” all the way up to 44”x69”.
- The MV-RF is available in set pressures ranging from 0.2 psig up to 10 psig.
- At set pressures at or below 2 psig, the MV-RF has a standard set pressure tolerance of +/- 0.25 psig.
- At set pressures above 2 psig, the MV-RF has a standard set pressure tolerance of +/- 0.5 psig.
- The MV-RF is rated for temperatures ranging from -20 degrees F all the way up to 150 degrees F.
- The MV-RF has a 60% operating ratio, meaning the MV-RF operates reliably and with a long service life at pressures up to 60% of the marked burst pressure. Pressure excursions above this 60% operating ratio will shorten the lifespan of the MV-RF.
- The MV-RF is available with a 1-year warranty as a standard.
- The MV-RF is available in all OE standard materials (316 Stainless Steel, Nickel 200, Inconel 600, Monel 400, and Hastelloy C 276). Other materials may be available or offered on request.
- The MV-RF utilizes a hinged opening design, ensuring it remains non-fragmenting.
- The MV-RF is capable of withstanding partial vacuum, at pressures down to -10 psig to -12 psig.
- The MV-RF is designed to meet all NFPA 61 and NFPA 68 requirements for explosion vents.
- The MV-RF can be paired with the SVT-03 sensor, to allow for remote monitoring of vent activation.
- For an 8”x8” MV-RF, the relief area is 54.0 square inches.
- For a 12”x12” MV-RF, the relief area is 129.0 square inches.
- For a 12”x18” MV-RF, the relief area is 196.0 square inches.
- For a 12”x24” MV-RF, the relief area is 264.0 square inches.
- For a 16”x18” MV-RF, the relief area is 266.0 square inches.
- For a 17.125”x17.125” MV-RF, the relief area is 272.0 square inches.
- For an 18”x24” MV-RF, the relief area is 405.0 square inches.
- For a 20”x24” MV-RF, the relief area is 452.0 square inches.
- For an 18”x28” MV-RF, the relief area is 474.0 square inches.
- For an 18”x30” MV-RF, the relief area is 508.0 square inches.
- For a 24”x24” MV-RF, the relief area is 546.0 square inches.
- For an 18”x35” MV-RF, the relief area is 595.0 square inches.
- For an 18”x36” MV-RF, the relief area is 612.0 square inches.
- For a 24”x30” MV-RF, the relief area is 685.0 square inches.
- For a 24”x36” MV-RF, the relief area is 825.0 square inches.
- For a 30”x30” MV-RF, the relief area is 862.0 square inches.
- For a 20”x48” MV-RF, the relief area is 914.0 square inches.
- For a 27”x36” MV-RF, the relief area is 931.0 square inches.
- For a 25”x40” MV-RF, the relief area is 957.0 square inches.
- For a 27”x39” MV-RF, the relief area is 1010.0 square inches.
- For a 24”x44” MV-RF, the relief area is 1011.0 square inches.
- For a 25”x43” MV-RF, the relief area is 1030.0 square inches.
- For a 27”x40” MV-RF, the relief area is 1036.0 square inches.
- For a 30”x36” MV-RF, the relief area is 1038.0 square inches.
- For a 24”x47” MV-RF, the relief area is 1081.0 square inches.
- For a 24”x48” MV-RF, the relief area is 1104.0 square inches.
- For a 27”x43” MV-RF, the relief area is 1115.0 square inches.
- For a 25”x47” MV-RF, the relief area is 1127.0 square inches.
- For a 25”x49” MV-RF, the relief area is 1176.0 square inches.
- For a 36”x36” MV-RF, the relief area is 1251.0 square inches.
- For a 30”x44” MV-RF, the relief area is 1272.0 square inches.
- For a 27”x52” MV-RF, the relief area is 1351.0 square inches.
- For a 30”x48” MV-RF, the relief area is 1389.0 square inches.
- For a 38”x38” MV-RF, the relief area is 1396.0 square inches.
- For a 27”x58” MV-RF, the relief area is 1509.0 square inches.
- For a 27.5”x57.1” MV-RF, the relief area is 1512.0 square inches.
- For a 36”x44” MV-RF, the relief area is 1533.0 square inches.
- For a 25”x66” MV-RF, the relief area is 1588.0 square inches.
- For a 27”x66” MV-RF, the relief area is 1719.0 square inches.
- For a 30”x60” MV-RF, the relief area is 1740.0 square inches.
- For a 42”x44” MV-RF, the relief area is 1794.0 square inches.
- For a 44”x44” MV-RF, the relief area is 1881.0 square inches.
- For a 44.5”x44.5” MV-RF, the relief area is 1925.0 square inches.
- For a 36×60” MV-RF, the relief area is 2097.0 square inches.
- For a 44”x60” MV-RF, the relief area is 2573.0 square inches.
- For a 42”x65” MV-RF, the relief area is 2660.0 square inches.
- For a 44”x69” MV-RF, the relief area is 2962.0 square inches.
- For an 8”x8” MV-RF, the minimum set pressure is 1.5 psig, and the maximum set pressure is 10.0 psig.
- For a 12”x12” MV-RF, the minimum set pressure is 1.4 psig, and the maximum set pressure is 10.0 psig.
- For a 12”x18” MV-RF, the minimum set pressure is 1.3 psig, and the maximum set pressure is 5.0 psig.
- For a 12”x24” MV-RF, the minimum set pressure is 1.3 psig, and the maximum set pressure is 5.0 psig.
- For a 16”x18” MV-RF, the minimum set pressure is 1.3 psig, and the maximum set pressure is 5.0 psig.
- For a 17.125”x17.125” MV-RF, the minimum set pressure is 1.3 psig, and the maximum set pressure is 5.0 psig.
- For an 18”x24” MV-RF, the minimum set pressure is 1.2 psig, and the maximum set pressure is 5.0 psig.
- For a 20”x24” MV-RF, the minimum set pressure is 1.2 psig, and the maximum set pressure is 5.0 psig.
- For an 18”x28” MV-RF, the minimum set pressure is 1.2 psig, and the maximum set pressure is 5.0 psig.
- For an 18”x30” MV-RF, the minimum set pressure is 1.2 psig, and the maximum set pressure is 5.0 psig.
- For a 24”x24” MV-RF, the minimum set pressure is 1.2 psig, and the maximum set pressure is 5.0 psig.
- For an 18”x35” MV-RF, the minimum set pressure is 1.2 psig, and the maximum set pressure is 5.0 psig.
- For an 18”x36” MV-RF, the minimum set pressure is 1.2 psig, and the maximum set pressure is 5.0 psig.
- For a 24”x30” MV-RF, the minimum set pressure is 1.1 psig, and the maximum set pressure is 5.0 psig.
- For a 24”x36” MV-RF, the minimum set pressure is 1.0 psig, and the maximum set pressure is 5.0 psig.
- For a 30”x30” MV-RF, the minimum set pressure is 1.0 psig, and the maximum set pressure is 5.0 psig.
- For a 20”x48” MV-RF, the minimum set pressure is 1.0 psig, and the maximum set pressure is 5.0 psig.
- For a 27”x36” MV-RF, the minimum set pressure is 1.0 psig, and the maximum set pressure is 5.0 psig.
- For a 25”x40” MV-RF, the minimum set pressure is 1.0 psig, and the maximum set pressure is 5.0 psig.
- For a 27”x39” MV-RF, the minimum set pressure is 1.0 psig, and the maximum set pressure is 5.0 psig.
- For a 24”x44” MV-RF, the minimum set pressure is 1.0 psig, and the maximum set pressure is 5.0 psig.
- For a 25”x43” MV-RF, the minimum set pressure is 1.0 psig, and the maximum set pressure is 5.0 psig.
- For a 27”x40” MV-RF, the minimum set pressure is 1.0 psig, and the maximum set pressure is 5.0 psig.
- For a 30”x36” MV-RF, the minimum set pressure is 1.0 psig, and the maximum set pressure is 5.0 psig.
- For a 24”x47” MV-RF, the minimum set pressure is 1.0 psig, and the maximum set pressure is 5.0 psig.
- For a 24”x48” MV-RF, the minimum set pressure is 0.9 psig, and the maximum set pressure is 5.0 psig.
- For a 27”x43” MV-RF, the minimum set pressure is 0.9 psig, and the maximum set pressure is 5.0 psig.
- For a 25”x47” MV-RF, the minimum set pressure is 0.9 psig, and the maximum set pressure is 5.0 psig.
- For a 25”x49” MV-RF, the minimum set pressure is 0.9 psig, and the maximum set pressure is 5.0 psig.
- For a 36”x36” MV-RF, the minimum set pressure is 0.8 psig, and the maximum set pressure is 5.0 psig.
- For a 30”x44” MV-RF, the minimum set pressure is 0.8 psig, and the maximum set pressure is 5.0 psig.
- For a 27”x52” MV-RF, the minimum set pressure is 0.7 psig, and the maximum set pressure is 5.0 psig.
- For a 30”x48” MV-RF, the minimum set pressure is 0.7 psig, and the maximum set pressure is 5.0 psig.
- For a 38”x38” MV-RF, the minimum set pressure is 0.7 psig, and the maximum set pressure is 5.0 psig.
- For a 27”x58” MV-RF, the minimum set pressure is 0.7 psig, and the maximum set pressure is 5.0 psig.
- For a 27.5”x57.1” MV-RF, the minimum set pressure is 0.7 psig, and the maximum set pressure is 5.0 psig.
- For a 36”x44” MV-RF, the minimum set pressure is 0.7 psig, and the maximum set pressure is 5.0 psig.
- For a 25”x66” MV-RF, the minimum set pressure is 0.6 psig, and the maximum set pressure is 5.0 psig.
- For a 27”x66” MV-RF, the minimum set pressure is 0.5 psig, and the maximum set pressure is 5.0 psig.
- For a 30”x60” MV-RF, the minimum set pressure is 0.5 psig, and the maximum set pressure is 5.0 psig.
- For a 42”x44” MV-RF, the minimum set pressure is 0.5 psig, and the maximum set pressure is 5.0 psig.
- For a 44”x44” MV-RF, the minimum set pressure is 0.5 psig, and the maximum set pressure is 5.0 psig.
- For a 44.5”x44.5” MV-RF, the minimum set pressure is 0.5 psig, and the maximum set pressure is 5.0 psig.
- For a 36×60” MV-RF, the minimum set pressure is 0.5 psig, and the maximum set pressure is 5.0 psig.
- For a 44”x60” MV-RF, the minimum set pressure is 0.3 psig, and the maximum set pressure is 5.0 psig.
- For a 42”x65” MV-RF, the minimum set pressure is 0.3 psig, and the maximum set pressure is 5.0 psig.
- For a 44”x69” MV-RF, the minimum set pressure is 0.2 psig, and the maximum set pressure is 5.0 psig.